The NEC requires I install 2-20amp circuits for a kitchen. I'm remodeling
my basement and installing a wet bar. It's not a kitchen, because there's
absolutely no provision for a stove. I'm not sure on what the NEC says abo
ut this situation. I can't find anything about wet bars except that I need
a GFCI within 6ft of a wet bar sink. I acknowledge that I can always do b
etter than the code, but does anyone know the rules for this case?
On Thu, 7 Jul 2016 20:16:21 -0700 (PDT), email@example.com wrote:
That is not a kitchen. Just use a GFCI on any receptacles you choose
to put near the sink and you are fine.
Article 100 definition
Kitchen. An area with a sink and permanent facilities for food
preparation and cooking.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.