On Mon, 30 Nov 2015 09:45:11 -0800 (PST), firstname.lastname@example.org wrote:
Short answer No
They are only listed for non-metalic cable. They are missing the
insulated throat a MC connector has. Used properly an NM connector is
isolated from the conductors by the cable jacket which should extend
1/4" into the box.
No, I was inquiring what the difference is by example of the only products
I'm familiar with (I've limited knowledge of the 100+ connectors in HomeDep
ot's catalog alone, much less the industry). Gfre...aol.com was nice enoug
h to offer the correct product and explain the difference and why I can't s
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.