I'm assuming that you "had" the furnace installed. I would call back the
installing company and have them check the indoor blower for paper or
something caught causing an unbalanced situation. If you're hearing the
inducer, perhaps something is out of balance there as well. Either way,
call your installing contractor back to check it.
"Martin Lewis" < firstname.lastname@example.org> wrote in message
Click to see the full signature.