I'm setting up a lampworking shop & need to ventilate it. Some folks
are using 350cfm range hoods. The ventilator I like that is actually
built for lampwork is 650cfm.
My son is going to build the hood-- and I have a squirrel-cage fan
that I think will move a lot of air. Is there any way to
guesstimate if I'm going to be in the 6-800 cfm range?
The motor is 1/6 hp, 2 speed- 1175rpm. [at fast speed?]
The cage is about 4inches across and 12 inches in diameter.
The hood will be 40x24x18inches [40x24 opening].
The ductwork will probably[I'm open yo suggestions] be 5' of 10" flex
for now. [3 horizontal and 2 vertical- no sharp bends]. In a fwew
months we move it all and it will be rigid ductwork- 1' through a
wall, then vertical to a cap.
On 17 Feb 2005 12:42:26 -0800, email@example.com wrote:
It is a real old, bulky, constant capacitor motor. [60's?] I
don't know if the rating system changed or what, but I have a slightly
older 1/12 motor that seems to of the work of a more modern 1/3hp
without bogging down.
That said-- should hp really have anything to do with the cfm's, or
are speed and fan size the determining factors on that end?
Direct-drive, .33HP electric motor features a spark- resistant 7.625-inch
impeller wheel. Runs at 1750 RPM; provides up to 1015 cubic feet per minute
of free air displacement @ O" static pressure. Other sizes available.
NOTE THE 0" static pressure!
further quote from page
The hood features a 10 " round discharge; this allows easy connection to
your in-house exhaust system to provide the internal negative pressure
necessary to safely remove fumes from the work surface. This hood is
completely noncontaminating and resists a wide range of corrosive materials;
select stainless or cold rolled steel.
Thanks - good idea.
I was real disappointed at first-- but the 12" in that case is overall
dimension. The blower is only 5 1/4".
Can't find any indication of how wide those wheels are, but on p590
there's a 1150rpm that is 10 5/8" diameter and has roughly the same
outlet size. It is blowing 1500-1870cfm. [and is powered by a 3/4 hp
motor!] I hope mine doesn't move that much air.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.