Mebbe coat this rubber ditty in some kind of silicone caulk (they make a
Silicone III?) or some flexible epoxy?
There's even a kind dip for plier handles that gives a very sturdy
Proly some other stuff. Pliobond adhesive?
Does this bellows thing wear in one place, or does it fail anywhere? This
could affect how you choose to coat/seal this thing.
Another possibility is make some kind of adapter, and just use a tougher
Ok... Some questions here...
Your generator is a little baby one compared to the 8 cylinder cat
generator sets I used to help the electrician maintain at the place I
(1.) How many hours of run-time do you experience between failures of
this particular part... Parts and service on generator sets are
in hours of running time rather than months or years...
(2.) What is the recommended service interval for that particular
hours? You stated that you had installed the generator after you
experienced a storm resulting in two weeks without power...
You haven't described how often the generator performs a "self-test"
and runs while switching the emergency loads to run from the
(3.) If this part is causing failures for your gen set why not
on a periodic basis even though it is not yet consumed? It is a $5
to ensure that back up power is available... I have seen thousands of
dollars worth of parts replaced annually on two huge cat diesel gen
to maintain their operational status even though the parts have not
Banks of batteries to start the generator were replaced every year in
the fall to ensure fresh good batteries would be available to crank
generator during the coldest of winter days even though the battery
pan was heated... These generators where integrated into the
building automation computer system so they were monitored by
many various sensors during their 20 minute exercise run time each
week down to the sine waveform the generator was putting out on each
phase and if some aspect was out of parameters the gen set could be
examined and serviced to make sure it was running in top condition
before it failed...
This sounds like an interesting thing to read up on in the service
for your gen set to see how often your failing part should be
Are you sure that there is not something unique to your generator's
installation that is causing this part to fail? Animals or insects?
Something environmental which could be weakening the rubber?
Generac has very explicit service intervals for some items, such as
spark plug, valve lash adjustment, etc. It makes no mention of this
particular part regarding preventative maintenance / replacement.
Weekly for 13 minutes per week.
I could and I will, but since Generac never recommends it, and the
Generac service technician who replaced the first one under warranty
seemed very surprised that it had failed in less than a year, blaming
it on "a faulty bellows rubber part which has been re-designed", I can
only assume that this is NOT supposed to fail this way. It is also a
PITA to replace and would be way better if it merely held up longer.
As a retired electrical engineer, I have read the owner's manual as
well as the service manual cover to cover. This item is not covered.
A chemist friend of mine opined that a variety of synthetic rubber
products are susceptible to airborne chemicals such as lawn pesticide
spray, and can weaken as a result. A possible explanation, and one
which prompts me to consider a silicone hump hose as a replacement.
Also could justify the approach of applying a coating to the bellows by
dipping it in some magic "goo" to coat the exposed surfaces. I consider
this explanation to be a bit of a stretch, but not entirely sure.
1) Frankly, at $5 per it's no exactly a bank breaking repair.
2) That said, from the picture is looks like it could handle a LOT of
vibration and relative motion between the carb and the air filter. I don't
think a simple hose would work or, worse, it would transfer too much force
between the two parts and damage one or the other.
3) and THAT said, since it connects the carb with the air filter, it would
operate with a slight negative pressure. You might try "repairing" an old
bellows or rein-forcing a new bellows with "liquid latex on the OUTSIDE.
You also might want to see whether the engine mounts are all sound. But it
looks like the vibration is sort of built into the design.
Thanks for your comments John. The $5 cost for the part is really
irrelevant. The frequent failures and the resulting loss of confidence
that this standby generator will truly work in the rare occasion when I
really need it are the big issue. And finding a way to avoid having to
replace this part every nine or ten months is the mission I have been
What I have (finally) learned is that the Generac "Master" technician,
sent out during the warranty period from a very old and established
Generac dealer in this area, made 2 huge mistakes.
The first mistake was to assume that the $5 rubber bellows was at fault
due to a defect in manufacture, telling me that a newer, improved part
was being installed. The folks at Generac tell me this was not true
The second mistake, and the crucial one, was that this same technician
made no effort whatsoever to see *****WHY**** it failed. I now see,
having taken apart and photographed the parts, and getting excellent
help here on this newsgroup, that the rubber bellows was being
distorted quite severely at rest, making it pre-loaded and distorted.
It turns out that there are some slotted adjustments to move one end of
the assembly around, thus allowing for correction of the misalignment.
This slotted alignment set-up is NOT mentioned in the owners manual or
the service manual. The technician apparently did not know that there
was an adjustment, and replaced the broken bellows with another one,
which then failed once again in less than a year. Had the root cause
been identified, I would have been spared all of the subsequent
replacements, all of which I have performed, assuming that the rubber
bellows was somehow weak or defective.
I briefly did install a "hump hose" made of silicone, before the
misalignment and adjustment option was discovered, and it appears that
this may have also "solved" the problem by providing a stronger
connection. But as others have pointed out here, and I observed, the
use of a hose, especially a stiffer and less compliant hose, transmits
a lot more vibration into the remaining parts, and is not an optimal
I think I have this problem solved, but the real test will be if I have
no further issues for the next several years. Other owners seem to be
getting very good reliability, and I hope to join the happy users now
that this is resolved.
This newsgroup has been an invaluable resource to me, and I am
sincerely very grateful for the really outstanding suggestions and
guidance. Thank you !!!
Lost meat from freezer: $475
Grandpa stroke, cost of ambulance ride $600
Grandpa's night in hospital $7542.36
Lost work at home office for two days $364.24
Motel room till Generac part comes $175
Yeah, it's only five bucks.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.