I'm running a 6-3 Romex NM-B with ground for my new air conditioner system.
My main panel doesn't seem to have any spare (unoccupied) 3/4" size punch outs left; but there is a 1/2" punch out. It is possible for me to fit this 6-3 with ground in there, but does anyone know whether this is prohibited by the NEC?
All advice (and NEC references) appreciated!
I doubt very much that this would meet Code. First of all, you can't just pass the cable
through the knockout hole -- for the protection of the cable and the connections, Code
requires some sort of fitting on the hole (e.g. a cable clamp aka "Romex connector") which
secures the cable to the box. And I can't imagine that any fitting which would fit a 1/2"
knockout is listed for use with anything as large as 6-3; for example, the Romex connectors
used with 1/2" knockouts are listed for 14-2 through 10-3.
Does the panel have any vacant 1" knockouts? Or can you ream the 1/2" hole to 3/4"?
On Monday, July 21, 2014 7:17:12 PM UTC-4, Doug Miller wrote:
Aside from that, does he really need #6 for an AC? Presumbably a home AC?
I have a 5 ton, which I believe is the largest made and it's rated for #8. I
wonder if he's sizing based on breaker, instead of sizing based on the
install instructions and eqpt rating. Meaning I have a 50 amp breaker on
my 8 gauge, 5 ton and it's to code because it's a motor load, not an oven.
On Mon, 21 Jul 2014 15:30:28 -0700 (PDT), email@example.com wrote:
Can you get the 6-3 cable through the required cable connector, is
the big question. If you can fit the 6-3 into the connector that
threads into the 1/2" knockout, you are gold. If not you will need a
knockout punch to enlarge the hole to 3/4" size (Greenlee punch)
I assume you mean a reamer - which leaves all kinds of conductive
swarf all through the panel. The only RIGHT way to do it is with a
"knoclut punch" - aften referred to by the most common brand - a
"greenlee punch" Any electrician worth his salt will have one. All you
get that way is a metal ring.
On 7/21/2014 8:31 PM, firstname.lastname@example.org wrote:
HF sells step bits which can be used to enlarge
the hole. Of course, you need a shopvac in action
at the same time to catch the chips.
Instead of a rimmer, use a knoclut punch. Amazing,
one good misssspelled word desserves anothher.
Christopher A. Young
Learn about Jesus
Whether he needs AWG-6 or AWG-8 is not really relevant -- neither one is listed for use with
any Romex connector or clamp that I'm aware of which will fit in a 1/2" knockout.
Another question for the OP: do you really need 6-3 (or 8-3, as the case may be) for an air
conditioner? If it's central AC, it's almost surely a pure 240V load, and 2-conductor cable will do
-- and if it's a window AC, 10-3 is almost surely sufficient.
but there is a 1/2" punch out. It is possible for me to fit this 6-3 with ground in there, but does
anyone know whether this is prohibited by the NEC?
WRONG. The big question is whether the required cable connector is listed for use with 6-3
cable. If the connector is not listed for use with 6-3 cable, it's a Code violation to use it for
that, whether the cable fits or not.
On Tue, 22 Jul 2014 01:14:05 +0000 (UTC), Doug Miller
Well, you show me a romex connector that will take a 6/3 cable that
isn't listed for use with 6/3 and you may have a point. The POINT is,
there is no romex connector that WILL accept a 6/3 - listed or not..
Hi, I'm the OP.
Yes, the mini split a/c system specs explicitly call for a 50amp breaker and #6 AWG (although I shudder to think that it'll actually use that much, with a 16 SEER).
I think I answered my own question by finding several "conduit fill charts" online that say 1/2" conduit can only have 2 #6 wires, so rules are there to keep me safe and I'm fine with that.
I also failed to notice one last 3/4" knock-out, so I'll be using that one.
Many thanks to all the good technical solutions and suggestions!
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.