I have a 3 way switch setpup at each landing for my basement stairs.
I replaced the three way switch at the top, and it is a combo switch.
Single pole/3 way. tWO LITE TERMINALS AND A COMMON. i WIRED THE TWO
WHITE WIRES TO THE LITETERMINALS AND THE BLACK TO COMMON. aLWAYS ON
SITUATION DEVELOPED. tRIED SWITCHING ONE WHITE FOR BLACK AND
DEVELOPED A SITUATION WHERE THE LIGHT TURNS ON AND OFFFROM THE NEW
SWITCH, NOTHING ON OTHER SWITCH. tHE OTHER SWITCH IS TWO SEPERATE
CIRCUITS, AND A SINGLE POLE/ 3WAY AS UPSTAIRS. tHE upstairs single
pole controls the outside light and works fine.
I have tried the two white and one black in all configs poss on the 3
way part of the switch. The two single pole wires are wired as
On 28 Mar 2007 19:15:14 -0700, email@example.com wrote:
Take a tester.
You will have one of the two situations.
One wire will be hot no matter what you do with the other 3-way
The other possibility will be that one wire will never be hot no
matter what you do with the other 3-way.
The wire you identify like this will go to the dark colored screw.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.