You guys are ridiculous with the free comments. Most online forums
are for just that - free advice. You guys run your forum like a bunch
of nazis, but that's OK, it's your forum.
Anyway, I had the system serviced today.
The primary was clogged and the emergency filled up to the water
switch so the switch would not let it engage.
Additionally, there was a bad connection on the transformer so the
tstat and outside contactor were not getting proper power.