I have a Gibson self contained GQ3R heatpump that has a defrost
problem. My question is, how do you diagnoise a defrost thermostat,
and how can you diagnoise the defrost board, or put the board into the
defrost mode without the defrost thermostat connected. I think the
defrost thermostat is a thermistor, is that correct?
If you were a tech, you would know how to run it though a test defrost
cycle. Just don't short the wrong terminals or you will be buying a lot more
than a DF board..... even if the problem is *only* the DF board.
Thanks Steve for a great answer! Just for the record I was a HVAC
contractor in the Nashville, TN area for 18 years and gave it up in
1989 for other interest. I know my way around the equipment very
well but am not familiar with the newer "to me" defrost board and
defrost thermostat. Almost every heat pump in that era used a
different way to do the same thing and it wasn't integrated onto a
single board. I can swap parts, but would like to diagnose before
throwing parts at it. By the way the board is part# 624633
Many Thanks, Everett
On Feb 17, 12:51 pm, email@example.com wrote:
On every board ive worked on, there are self test pins that you jumper
to put the unit into defrost initiation and defrost termination
modes . Im afraid that there are so many boards out there that a
Model Unit brand or part number on the board is of little help. Best
thing is to either get a manufacturers checkout procedure sheet or
find a local HVAC guy who has worked on these units who wont mind
sharing his knowledge with you. In closing, oftentimes when you look
at the board there will be 2 or 3 pins that are marked 'Test' near
them --- these are most likely the test pins for sending the unit into
defrost . I miss the old Ranco mechanical type Defrost Control that
was simply to engage defrost as well as troubleshoot .. such is
progress i guess. Regards.
On Fri, 25 Feb 2011 07:53:28 -0800 (PST), " firstname.lastname@example.org"
Thanks for the reply, I found the answer on the Nordyne site. Nordine
is the manufacturer of the Gibson line. There have been a bunch of
upgraded defrost boards since the date of manufacture on my unit, but
I think the test method is at least the same since my board, as the
test method I used was for a newer unit. There is an area at the lower
left of the board that has three terminals. They are marked ( T2 - Def
- test ). Using these terminals you put a jumper between T2 and
defrost with the unit in heat mode and running, then jump between test
and C to enter test mode, removing test - C connection as defrost test
starts. To stop test remove jumper between T2 and defrost.
Your right about the old Ranco board, I use to work on all brands and
would scratch my head on many ocassion wondering why every
manufacturer would do the same thing a different way,
On Feb 25, 12:45 pm, email@example.com wrote:
Glad you got your answer. Actually, I wasnt referring to the Ranco
Defrot Board, but, the old Ranco E15 mechanical type Defrost Controls
as thus : http://thermatixsupply.com/index.php?dispatch=products.view&product_id=30821
. It was nice and simple and you could run the Heat Pump Unit into and
out of defrost cycle by manually turning the Timer .
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.