inducer motor runs, igniter lites then goes out then the fan motor comes
on but no flames. Any Ideas? I installed new propoane tanks and regulator.
I do not hear the relay click for the valve for the flames.and yes propane
See if voltage is applied to the gas valve at the
appropriate time during the ignition cycle. If not find out
why such as loose connectors, bad control board,
differential pressure sensor, thermal fuse, manual reset
button, etc. This is not difficult if you understand the
basic operation of the unit and its safety check features.
If voltage is present, check the continuity of the valve
solenoid. If open, replace the valve. If not open, check gas
pressure at the valve input. If none fix the no pressure
problem. If present, call one of the hacks that post on this
group that will sell you a new furnace and then wonder why
it does not ignite.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.