I need something to add to my water pipes to stop the loud 'bang' when the
dishwasher inlet valve suddenly shuts or when someone closes a tap quickly.
I believe there are small air vessels that can be fitted to water pipes:
1. Who sells these?
2. Are they effective?
3. On what part of the system (i.e. inlet stoptap, last takeoff on system)
should they be fitted for best effect?
Have you tried turning the cold water mains inlet stop tap down a shade.
|I need something to add to my water pipes to stop the loud 'bang' when the
| dishwasher inlet valve suddenly shuts or when someone closes a tap
| I believe there are small air vessels that can be fitted to water pipes:
| 1. Who sells these?
| 2. Are they effective?
| 3. On what part of the system (i.e. inlet stoptap, last takeoff on system)
| should they be fitted for best effect?
Near the source of the shock, except when it shouldn't be, or
near the stopcock, except when it shouldn't be, or
near any other volume reducing restriction in your pipework, except . . . .
oh I'm sure you get the idea . . .
What I'm trying to say is yes they can be effective, but placement can be
problematic for full effectiveness. In the case where you have a single item
turning off quickly and causing a shock wave, then placing the arrestor on
the fixed pipework within a foot of the dishwasher connection will probably
be effective. Placing it at the stopcock may also be effective and has the
advantage that it should arrest shock waves from other taps/appliances.
They are normally the solution of last resort so before trying one I would
tightly fix all pipework in the (kitchen) area with pipe clips to see if the
problem is reduced and as Stickems said, try turning down the stop cock
I would think something like what you're suggesting would be a better idea.
Unless those contraptions have a bladder they'll fill up with water
You could build something that may end up being more expensive depending on
materials used. But you could design it to be able to be drained. Which
would probably limit where you put it.
Short answer: Yes. :)
Yes Steve thats the way to do it. turning down the tap wont cure it it is
caused by ripples in the (nornmaly plastic)storage tank turning the water on
and off this asabates the effect causeing reciplical vibration in the pipes.
air in an up right piece of pipe work will damp this down. Tried it and it
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.