I have a 2 year old towel rail fitted by a plumber. It worked really
well up until this autumn.
Although one of the pipes below the rail gets hot, the rail itself
never does despite the fact that both valves are fully open. I've
tried bleeding it (gets warm for half an hour), I've tried
disconnecting and re-filling it (same thing). Oddly both pipes seem to
be pumping water into the system rather than one pumping and one
Short of threatening it with violence or reading it poetry I'm out of
Any suggestions would be welcome.
(it seems to work in the summer as well as the winter...so I'm guessing
its not connected directly to the central heating system)