I've having a new kitchen fitted next year, and as a part of it I want to
replace my existing radiator with a narrow vertical type to free up some
My cirrent radiator is a double raiator which is 175cm wide and 70 cmhigh.
Any idea if there's a general rule of thumb to get its heat output (BTU or
kW) ? as I want to get a very differently styled radioator but want the same
Or, alternatively...the room is 4.5m x 3.5m. What sort of output from a
radiator would I want here?
Look at a site supplying radiators and compare radiators of similar
configuration (single/double) and size, the output will be quoted beside the
size. Watts are the 'new money' of specifying heat output.
Try http://www.discountedheating.co.uk /
The make of rad has little to do with the heat o/p compared with the
Thanks for the link. I have looked at my kitchen rad and it has no
'convector' bits between its two panels, so I wouldl classify it as a 2
panel, no convector.
I cannot finr this type or rad on the web, as all two-panel rads have
convector fins between the panels. How can I guestimate my rad's output
compared to a 2-panel single convector on the web?
Same, more, or less?
Wow, that's an old one, it's very unusual to find one w/o convectors these
The convectors make quite a difference but if you could find data for a
single panel radiator (ie one w/o a convector) you could take a guess at it
being just under twice the o/p from a single.
Although very few people sell singles (w/o convectors) the data will still
likely be found on manufacturer websites and http://www.stelrad.co.uk
would be a good place to start.
I've got the data here so here's a sample for Stelrad Elite radiators:
K2 (double convector) 2266W
P+ (double panel with single convector) 1795W
K1 (single convector) 1265W
P1 (single panel - no convector) 775W
The output from a double panel will be less than the P+ ie 1795W but
probably greater than the single convector (K1) 1265W, our guess of 2x
single panel would make 1550W but I reckon it would be a little less as the
2 panels are in close proximity, lets say 1450W.
From that little fiddle we have that a double panel will have an output of
roughly 65% of a similarly sized double convector.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.